- Prepping Basics
- Survival Basics
- Prepper Resources
- Contact Us
Editor’s Note: This post is another entry in the Prepper Writing Contest from Lancer. If you have information for Preppers that you would like to share and possibly win a $300 Amazon Gift Card to purchase your own prepping supplies, enter today.
A perennial problem faced by suburban and rural dwellers is obtaining water in the absence of utility provided electric power. Standby generators require fuel of some type, which will eventually run out, and deep drilled wells are poorly suited for use with hand pumps of most types.
As a prepper this has always been a concern for me as I live in a rural setting, but in a house constructed with the modern “central-everything” design concepts. I do have a gasoline powered generator, and maintain supplies enough for a few weeks of continuous running. After that it’s carrying buckets to the stream.
This has led to my experimenting with some alternatives for my survival homestead, and based upon my current deployment I may just go off grid for water completely. Most of the components I had lying around with the exception of the pump, and the batteries: those items set me back around $450.
So the conundrum is: how to extract perfectly clean water from this well at minimum cost, and without completely changing the plumbing. (I may want to sell and move further out, so any new owner will probably want things as standard as possible)
What I have come up with to date, experimental at this point is a solar/battery-powered pump that stores water in an elevated container, allowing gravity to supply the pressure. Keep in mind though: water is heavy! Be sure to reinforce your structure as needed! I’d consider this a relatively high level overview as opposed to a design doc, so tailor as needed for your own situation.
The first thing is to install the new pitless adapter in the well casing, just follow the instruction that came with it, In my case I needed a 1-3/4” hole saw.
Using a string with a weight on it find the depth of the torque arrestor above the standard pump.
Using the same string with a float find the water level in the well casing.
Cut a piece of PEX approximately three feet shorter that the depth of the torque arrestor but be sure it’s still well below the water height. If it very close you may have to re-examine the well suitability.
Connect the two conductor wire to the new pump following the instructions meticulously: you do NOT want the fitting to leak.
Connect the piece of pex to the new pump. Use stainless clamps or crimp collers.
Connect the PEX to the pitless adapter using suitable adapter hardware.
Run a piece of paracord through the lifting eye on the pump, either use twice the needed length so you can pull it free later, or a bowline if you want to keep it in place.
Secure the line to something sturdy, it’s there in case the pump slips out of your hands.
Drop the pump and attached wire down the well. Be very sure it doesn’t come to rest on the torque arrestor! If it does, pull it and adjust the length of the PEX.
Install the solar array where ever you want: mine are on a south-facing roof with a 45 degree pitch.
Install the solar panel charge converter somewhere out of the weather; connect the wiring as described in the instructions.
Run #8 stranded wires from the charge converter to the battery bank.
Turn the charge converter on and make sure the batteries are charging. A voltmeter is sufficient. Mine reads 13.8VDC across the battery terminals in bright sun.
Connect the new well wires to the batteries to ensure the pump works correctly.
If yes, disconnect the pump for now.
Connect the remaining PEX to the pitless adapter outlet, tape the pump wire to the PEX, and bury the entire run below the frost line for the area.
Run it into your basement or crawlspace using whatever critter-proof method you wish.
Install a large water container in a location above your typical faucet height. The higher the location the greater the water pressure.
I’ve been experimenting with a water-bed mattress because, 1 – I had it already, 2 – it distributes weight well.
Run the PEX and wiring up to whatever storage container you are using, install the check valve, (flow toward the storage tank!), then the PEX Tee after the check valve, and then from the check valve outlet side into the tank, using suitable fittings to provide for a secure, leak free connection. Inside the container, if it’s not flexible like the mattress, install an addition piece of tubing that just barely reaches the bottom of the container.
Install the limit switch with a float or similar to open the pump circuit when the water level reaches the maximum desired height in the container. Typically you would use the normally closed contacts that will open when the float is lifted. There is a multitude of ways to do this, I happened to have the switches already.
Now run the wiring to the batteries, and connect, observing the correct polarity as during the initial test.
On the original house water supply plumbing cut and insert a tee in the line from the pressure tank going to the house plumbing. Install one of the gate valves in the Tee side going to the new storage. The object is to connect the new storage container outlet Tee to the standard supply plumbing after the pressure tank check valve, see drawing 4.
The content on the Prepper Journal is provided as general information only. The ideas expressed on this site are solely the opinions of the author(s) and do not necessarily represent the opinions of anyone else. The author may or may not have a financial interest in any company or advertiser referenced. Any action taken as a result of information, analysis, or advertisement on this site is ultimately the responsibility of the reader.
The Prepper Journal is a participant in the Amazon Services LLC Associates Program, an affiliate advertising program designed to provide a means for sites to earn advertising fees by advertising and linking to Amazon.com.